Where is the EASYsafe used
It is common practice to protect multiple end load circuits through a single switch board circuit breaker backed up by RCDs.
This only translates into multiple end loads being disconnected by the operation of the protection system in the event of a fault on a single device, bringing down the entire system.
This can have a significant impact on end users in the event of a fault and can add a level of complexity to fault finding as well as endanger mission critical systems.
The EASYsafe protects a single circuit to the attached equipment and its user and all other installed devices remain on line.
How is the EASYsafe used
1. For surface mounting, remove the two securing screws on the front panel.
2. Affix the enclosure base via the 4 corner holes and fit the plastic covers.
3. Refit the enclosure front panel with the 2 screws from (1) above
4. Ensure that the circuit breaker switch is in the OFF (down) position.
5. Connect the IEC C14 plug to the mains 240 volt A.C. power.
6. Switch power on at the mains power wall outlet.
7. Swith the circuit breaker to the on position (UP)
8. Test the Residual Current Safety Switch as below.
9. Connect the load to the IEC C13 socket.
To ensure that the RCD Safety Switches fitted to equipment perform correctly, they must be tested at regular intervals. AS/NZS 3760 2010 recommends that each RCD be tested every three months.
To test the RCD Safety Switch press the test button on the front of the device and then release it. Pressing the test button will simulate an earth leakage fault and indicates whether the device is operating correctly.
When an RCD Safety Switch operates all power is lost to the equipment protected by the RCD. To restore power simply move the on/off switch back to the on position.
- Universal IEC mains connections, NO ELECTRICIAN needed
- ES240-RCBO over all size 170mm x 75mm x 90mm
- Weight approx. 250g. packaged
- Circuit breaker overload rating 10 amp with 4500 amp breaking capacity.
- Circuit breaker type is C curve magnetic tripping
- Over-voltage surge current capacity: In = 20kA with Imax = 40kA
- RCD has residual earth leakage detection of 30 ma.
- Conforms to ASNZS 61009.1, C-tick, ROHS and CE certification.
- Complies with Energy Safe Victoria’s additional RCBO testing and
verification requirements as of 1st July 2018
- We Design and Manufacture Professional Electronic Equipment
- Trusted supplier to Government, Industry and Consumers for 40 years
- Buy with Confidence from Australian Designer and Manufacturer.
- ANY ENQUIRIES PLEASE EMAIL email@example.com